From: Larry Sheldon (no email)
Date: Fri May 14 2010 - 20:17:40 EDT
On 5/14/2010 19:00, Seth Mattinen wrote:
> On 5/14/2010 16:42, Ingo Flaschberger wrote:
>>>> We had a lightning strike nearby yesterday that looks to have come
>>>> inside our facility via a feeder circuit that goes outdoors
>>>> underground to our facility's gate.
>> Perhaps there was a "move" of the earth-level relative to the neutral line.
>> I have no idea how neutral-line to earth potential is handled in us, but
>> here in austria we use a so called "nullung".
>> That means that the earth-ground potential line of the building (which
>> includes also the lightning conductor) is connected to the neutral power
>> line where it enters the building, keeping this potential-difference low.
> In the US neutral and earth ground are supposed to be bonded only once
> at the service entrance. A separate ground from the neutral conductor is
> carried to sub-panels where is it not bonded. Additional bonding can
> cause weirdness and will turn the ground into a current carrying
> conductor. However, an older building I used to be in (built 1978) only
> gave me a neutral with bonded subs, so you'll run into all kinds of
> stuff depending on the age of the building. Working at a university was
> particularly interesting with of the vast range of building ages.
In my experience, each building has a building ground-point at the
service entrance, as outlined.
I the problem in a campus on some soils is that building grounds might
be several volts apart--except during thunder storms when the voltage
difference might be (it appears) thousands of volts, and with a
lightning strike to one of them many thousands of volts.
That is why I argue for glass only between buildings. I don't care how
much PoE saves.
-- Somebody should have said: A democracy is two wolves and a lamb voting on what to have for dinner. Freedom under a constitutional republic is a well armed lamb contesting the vote. Requiescas in pace o email Ex turpi causa non oritur actio Eppure si rinfresca ICBM Targeting Information: http://tinyurl.com/4sqczs http://tinyurl.com/7tp8ml